1. Flange connection.
Pipes with larger diameters are connected by flanges. Flange connections are generally used in main road connecting valves, return valves, water meter pumps, etc., as well as on pipe sections that need to be dismantled and repaired frequently. If the galvanized pipe is connected by welding or flange, secondary galvanizing or anti-corrosion shall be carried out at the welding place.
Welding is suitable for non-galvanized steel pipes, mostly used for concealed pipes and pipes with larger diameters, and is widely used in high-rise buildings. Copper pipes can be connected by special joints or welding. When the pipe diameter is less than 22mm, socket or sleeve welding should be used. The socket should be installed against the flow direction of the medium. When the pipe diameter is greater than or equal to 2mm, butt welding should be used. Socket welding can be used for stainless steel pipes.
3. Threaded connection.
Threaded connection is to use threaded pipe fittings to connect, and galvanized steel pipes with a pipe diameter less than or equal to 100mm should be connected with threads, which are mostly used for exposed pipes. Steel-plastic composite pipes are also generally connected with threads. Galvanized steel pipes should be connected by threaded connections, and the surface of the galvanized layer and exposed threaded parts that are damaged during threading should be treated with anti-corrosion; flanges or ferrule-type special pipe fittings should be used for connection, and the welds between galvanized steel pipes and flanges should be two Secondary galvanized.
4. Socket connection.
For connection of water supply and drainage cast iron pipes and fittings. There are two types of flexible connection and rigid connection. The flexible connection is sealed with a rubber ring, the rigid connection is sealed with asbestos cement or expandable packing, and lead sealing can be used in important occasions.
5. Card sleeve connection.
Aluminum-plastic composite pipes are generally crimped with threaded ferrules. Put the fitting nut on the end of the pipe, then put the inner core of the fitting into the end, and tighten the fitting and the nut with a wrench. The connection of copper pipes can also be crimped with threaded ferrules.
6. Press connection.
The stainless steel compression pipe fitting connection technology replaces the traditional water supply pipe connection technology such as threading, welding and gluing. It is connected with the pipeline, and the brick anus presses the nozzle to play the role of sealing and fastening. It has the advantages of convenient installation, reliable connection and economical rationality during construction.
7. Hot melt connection.
The connection method of the PPR pipe adopts a hot melter for hot melt connection.
8. Groove connection (clamp connection).
The groove type connector can be used for fire fighting water, air conditioning cold and hot water, water supply, rainwater and other systems with a diameter greater than or equal to 100mm galvanized steel pipe. It has simple operation, does not affect the original characteristics of the pipeline, safe construction, and good system stability. , Easy maintenance, labor-saving and time-saving features.
Post time: Aug-10-2022